In this month's home inspection pictures, we are going with an electrical theme. In the first picture we see a meter box for a service lateral (underground electrical service). This can be a real safety issue, especially if there is not a frost sleave on the conduit. Moisture intrusion can also be a big problem here. In the second picture we see an outlet tester with a single light on it, which means it is an open ground outlet. If you have a 3-prong outlet, be sure it is properly grounded. Questions? Contact me!